AWWA C Fiberglass Pressure Pipe, Includes Errata (). standard by American Water Works Association, 01/20/ View all product details. ASTM D and AWWA C requirements. Strain Corrosion Testing. A unique and important performance requirement for GRP gravity pipe used in sewer. PIPE AWWA Cpdf – Download as PDF File .pdf) or read online.
|Published (Last):||15 February 2015|
|PDF File Size:||3.16 Mb|
|ePub File Size:||7.91 Mb|
|Price:||Free* [*Free Regsitration Required]|
Methods of computing appropriate deflection values for other pipe stiffness levels have been added Sec. If a water pipe must pass through such a contaminated area or an area subject to contamination, consult with the manufacturer regarding permeation of pipe walls, jointing materials, and so forth, before selecting materials for use in that area.
Fiberglass Pipe Conforming to Awwa C950 Standard
A polymer containing two or more three-mem- bered rings, each consisting of one oxygen and two carbon atoms. Proceed to Checkout Continue Shopping. Tapered bell and straight spigot: Thus, users of this standard should consult the appropriate state or local agency having jurisdiction in order to 1.
Subsequent polymerization of the resin system may require application of heat. The pipe shall be filled with water, expelling all air, and an internal water pressure wawa be applied at a uniform rate until a pressure of two times the pressure class is reached see Table 7. Purchasers of American National Standards may receive current information on all standards by calling or writing the American National Standards Institute, 11 W.
The action becomes effective on the first day of the month following the month of Journal AWWA publication of the official notice. The types, grades, and liners are identified in the following paragraphs. In the broad sense, the term is used to designate any polymer that is a basic material for plastics.
The AWWA standards usually contain options that must be evaluated by the user of the standard. Unless otherwise agreed on by the purchaser and supplier, the manufacturer shall perform hydrostatic c9500 tests to all pipe sizes 1 in. A particular type of joint may be restrained or unrestrained and flexible or rigid depending on the specific joint configuration and design conditions.
AWWA C950 SPECIFICATIONS FOR FIBERGLASS PRESSURE PIPE
Glass-fiber-reinforced epoxy mortar RPMP epoxy. The specification of FRP pipe: This is a visual observation for quality control purposes only and should not be considered a simulated service test.
Service and distribution piping systems and transmission piping systems are included. This standard may be used to the extent applicable for other sizes, pressure classes, and stiffness classes. Sr is the calculated hoop tensile stress at the pressure class.
Subscription pricing is determined by: Enter the email address you signed up with and we’ll email you a reset link. Please first verify your email before subscribing to alerts.
Required axial strength for aboveground pipes subject to beam bending, or any pipes that must withstand longitudinal thrust loads or any unusual axial tensile forces, may exceed the values in Table Acceptance in the foreword for additional guidance.
If a manufacturer desires to exclude inspection of proprietary manufacturing processes, the manufacturer shall so advise the purchaser. Some variations from this format may be found in a particular standard. C Modification to Standard Liner materials incorporated include thermosetting or thermoplastic resin, reinforced or unrein- forced, with or without fillers. Cooling water GRP piping systems. Pipe joint capable of withstanding internal pressure and longitudinal tensile loads.
Each of the two samples shall conform to the requirements specified. Glass-fiber-reinforced epoxy RTRP epoxy. We have no amendments or corrections for this standard.
AWWA C – Fiberglass Pressure Pipe
Specific policies of the state or local agency. The pipe shall be as uniform as commercially practicable in color, opacity, density, and other physical properties. Purchaser Options and Alternatives.
A filled or unfilled thermoplastic or thermosetting resin layer, nonreinforced or reinforced, that forms the interior surface of the pipe. Standards Subsctiption may be the perfect solution. The party that manufactures, fabricates, or produces materials or products.
Process GRP piping systems 3. The end of a pipe test specimen with an end closure configuration such that internal pressure produces only hoop and radial stresses in a straight pipe test specimen. Standards Subscriptions from ANSI provides a money-saving, multi-user solution for accessing standards.
These include heat tracing to awa the medium from freezing. As the voice of the U.
AWWA C Specs – Beetle Plastics
As the voice of the U. Pipe diameters and tolerances shall be as shown in Tables 1, 2, 3, 4, 5, and 6 when measured in accordance with ASTM D The purchaser may also specify the following: Use of This Standard. A fiberglass pipe without aggregate. The test data should be statistically extrapolated to establish strength at 50 years.
The pipe stiffness test specimen may be used for these tests. Auxiliary GRP piping systems 4. All joints shall meet the Laboratory Performance Requirements of Sec.